What is Pressure Piping?
Pressure piping is any piping that carries fluid under internal or external pressure. ASME B31 serves as the design code for pressure piping. All process piping, power piping, pipelines all are examples of pressure piping.
What is High Pressure Piping?
High pressure piping is the piping that owner designate as being high pressure fluid service. Appendix IX of ASME B 31.3 provides design rules for High Pressure Piping. These rules are slightly different from normal presure piping. However, in this article we are not discussing about this piping systems.
High Temperature and High-Pressure Piping
With an increase in temperature and pressures, piping systems become more and more critical from a stress point of view. So, Piping Stress Engineers have a real tough time to qualify all there systems as material allowable drops with an increase in temperature. This article will try to list down the impacts that these two process parameters impart in piping stress systems.
Major Characteristics of High Temperature and High Pressure Piping
With respect to high temperature and high-pressure conditions in piping, the following are the typical features-
Higher the pressure in the pipe, the higher is the thickness of the pipe. Higher thickness means more rigid and less flexible. All these cause a higher load on the supports, higher frictional component acting axially and laterally, which in turn can cause higher loads on the equipment nozzles.
Higher the temperatures, higher are the pipe movements – vertical, axial, and lateral. This also causes higher frictional forces in the system. At the same time, high-temperature piping have low allowable stresses as with an increase in temperature material allowable stress value reduces. So the qualification of stress systems becomes more difficult.
Due to high movements, there are high strains and stresses in the piping system. This, in turn, leads to higher forces and moments on the supports and equipment nozzle.
Pipe supporting becomes complicated with the need to use special type supports like spring hangers, snubbers, anti-friction slide plates, etc. Also, with an increase in thermal movement long shoe supports come into the picture.
Depending upon the layout limitation use of expansion joints may become essential. Expansion joints are very expensive and difficult to maintain. Design Life of expansion joints is normally very less as compared to the piping systems.
The higher the temperature, the lesser is the allowable strength of the material. Consequently the more, the pipe and fittings will become prone to failure. The valves, gaskets, studs, etc. have to be of material to withstand that high temperature.
The choice of Studs/ bolts materials becomes important at high temperatures.
For lines with high operating temperatures, hot bolting is done to take care of the expansion of the bolts at that high temperature.
Another thing that needs to be considered is the relaxation of bolts over a period of time. Special washers might be required to be used in such cases.
Welding external attachments/ appurtenances on very high-temperature pipes can cause thermal differential and induce cracking in the attachments.
During plant start-up, there is a possibility of two-phase flow in long pipes seeing high temperatures leading to thermal bowing.
At very high temperatures, the line may operate in creep range leading to permanent yielding of the materials. Thus such piping when cooled down during plant shutdowns does not come back to the original position of the piping. This is termed as the phenomenon of Thermal shakedown.
The material selected for high temperature and high-pressure piping should be resistant to corrosion at higher temperatures.
As the temperatures increase in high-temperature piping systems, the insulation thickness is increased. Also at temperatures of the order of 650-700 degree C, Ceramic wool is to be used instead of Rockwool which is used for normal 300-400 degree C piping. More insulation thickness means more weight loads in the system.
In places where the pipe displaces to a high degree over supports, cold pulls or offsets might be required.
Examples of High Temperature Piping Systems
Few examples of the high-temperature piping system are listed below:
- The Aromatics Platformer Reactor lines are at a temperature of about 520 degrees C
- The Slop Wax / Vacuum Residue lines from the bottom of Crude Column are at a temperature of 424 degrees C
- The Vacuum Column – Heater Transfer line from the Vacuum Heater to the Vacuum Column is at a temperature of 396 degrees C
- The FCCU Flue Gas line going to the Expander – Power Recovery Train at a temperature of 714 degrees C
- In Coker, the coke cutting (hydro-jetting) lines see a pressure of 350 kg/cm2.
- In Vacuum Gas Oil Unit the Reactor Circuit has lines with 360 degrees C and 97 kg/cm2
- In CPP the Turbine lines at a temperature of 524 degrees C and Pressure of the order of 126 kg/cm2.
- The typical HP Steam (High-Pressure Steam) system has a temperature of up to 400 degrees C and pressure approximately 45 kg/cm2.
- The typical MP Steam system has a temperature of up to 260 degrees C and pressure approximately 18 kg/cm2.
- The typical LP (Low-Pressure) Steam system has a temperature up to 200 degrees C and pressure approximately 5 kg/cm2.
Based on the temperatures and the pressure in the piping, the material of construction needs to be selected.
- Carbon Steel can be used up to 427 degrees C
- Alloy Steel can be used up to 650 degrees C
- Stainless Steel can be used up to 550 degrees C
Few more Resources for you..